Workplace investigations of ventilation systems may be initiated by worker complaints of possible overexposures to air contaminants, possible risk of fire or explosion from flammable gas or vapor levels at or near the lower explosive limit (LEL), or indoor air quality complaints. The second phase of the investigation involves an examination of the ventilation system's physical and operating characteristics.
B.FAULTY VENTILATION CONDITIONS AND CAUSES.
Common faulty ventilation conditions and their probable causes are listed in Table III:3-1. Specific points to consider during any investigation of a ventilation system include emission source, air behavior, and employee involvement. Points that should be included in a review of operational efficacy are shown in Table III:3-2. Appendix III:3-4 contains information on points to be checked in a troublesome exhaust system.
C. BASIC TESTING EQUIPMENT might include:
- smoke tubes
- velometers, anemometers:
- - swinging vane anemometer
- - thermal or hot-wire anemometer
- pressure-sensing devices:
- - U-tube or electronic manometers
- - Pitot tube
- - thermal (thermal and swinging vane instruments measure static
- pressure indirectly)
- - aneroid ("bellows") gauges
- noise-monitoring equipment
- measuring tapes
- other: rags, flashlight, mirror, tachometer
- combustible gas meter or oxygen meter
- tubes for CO, CO2, formaldehyde, etc.
The characteristics of the ventilation system that must be documented during an investigation include equipment operability, physical measurements of the system, and use practices.
E. EQUIPMENT OPERABILITY
Before taking velocity or pressure measurements, note and record the operating status of the equipment. For example, are filters loaded or clean? Are variable-flow devices like dampers, variable-frequency drives, or inlet vanes in use? Are make-up units operating? Are system blueprints available?
- Duct diameters are measured to calculate duct areas. Inside duct diameter is the most important measurement, but an outside measurement is often sufficient for a sheet metal duct. To measure the duct, the tape should be thrown around the duct to obtain the duct circumference, and the number should be divided by (3.142) to obtain the diameter of the duct.
- Hood and duct dimensions can be estimated from plans, drawings, and specifications. Measurements can be made with measuring tape. If a duct is constructed of 2½ or 4-foot sections, the sections can be counted (elbows and tees should be included in the length).
- Hood-face velocities outside the hood or at the hood face can be estimated with velometers, smoke tubes, and swinging-vane anemometers, all of which are portable, reliable, and require no batteries.
a. The minimum velocity that can be read by an anemometer is 50 feet per minute (fpm). The meter should always be read in the upright position, and only the tubing supplied with the equipment should be used.
b. Anemometers often cannot be used if the duct contains dust or mist because air must actually pass through the instrument for it to work. The instrument requires periodic cleaning and calibration at least once per year. Hot-wire anemometers should not be used in airstreams containing aerosols.
c. Hood-face velocity measurement involves the following steps:
- mark off imaginary areas;
- measure velocity at center of each area; and
- average all measured velocities.
d. Smoke is useful for measuring face velocity (see Figure III:3-2) because it is visible. Nothing convinces management and employees more quickly that the ventilation is not functioning properly than to show smoke drifting away from the hood, escaping the hood, or traveling into the worker's breathing zone. Smoke can be used to provide a rough estimate of face velocity:
FIGURE III:3-2. USE OF SMOKE TO DEMONSTRATE AIR FLOW.
Velocity = Distance/Time , or
Squeeze off a quick burst of smoke. Time the smoke plume's travel over a two-foot distance. Calculate the velocity in feet per minute. For example, if it takes two seconds for the smoke to travel two feet, the velocity is 60 fpm.
- Hood static pressures (SPH) should be measured about 4-6 duct diameters downstream in a straight section of the hood take-off duct. The measurement can be made with a pitot tube or by a static pressure tap into the duct sheet metal (see Figure III:3-3).
FIGURE III:3-3. USE OF STATIC PRESSURE TAP INTO DUCT TO MEASURE HOOD STATIC PRESSURE.
- ELEMENTS OF A GOOD MAINTENANCE PROGRAM.
PUT IT ON PAPER
- Establish a safe place to file drawings, specifications, fan curves, operating instructions, and other papers generated during design, construction, and testing.
- Establish a program of periodic inspection.
a. The types and frequencies of inspections depend on the operation of the system and other factors.
- Daily: Visual inspection of hoods, ductwork, access and clean-out doors, blast gate positions, hood static pressure, pressure drop across air cleaner, and verbal contact with users. ("How is the system performing today?")
- Weekly: Air cleaner capacity, fan housing, pulley belts.
- Monthly: Air cleaner components.
b. A quick way to check for settled material in a duct is to take a broomstick and tap the underside of all horizontal ducts. If the tapping produces a "clean" sheet metal sound, the duct is clear. If the tapping produces heavy, thudding sounds and no sheet metal vibration, liquids or settled dust may be in the duct.
- Establish a preventive maintenance program. Certain elements of any ventilation system should be checked on a regular schedule and replaced if found to be defective.
- Provide worker training. Workers need to be trained in the purpose and functions of the ventilation system. For example, they need to know how to work safely and how best to utilize the ventilation system. Exhaust hoods do little good if the welder does not know that the hood must be positioned close to the work.
- Keep written records. Maintain written documentation not only of original installations but also of all modifications as well as problems and their resolution.
- DEALING WITH MICRO-ORGANISMS. If you suspect microbial agents, check for stagnant water in the ventilation system. The presence of mold or slime is a possible sign of trouble. Table III:3-4 lists preventive measures for controlling microbial problems in ventilation systems.
TABLE II:3-4. PREVENTIVE MEASURES FOR
REDUCING MICROBIAL PROBLEMS IN BUILDINGS
- Prevent buildup of moisture in occupied spaces (relative humidity of 60% or less).
- Prevent moisture collection in HVAC components.
- Remove stagnant water and slime from mechanical equipment.
- Use steam for humidifying.
- Avoid use of water sprays in HVAC systems.
- Use filters with a 50-70% collection efficiency rating.
- Find and discard microbe-damaged furnishings and equipment.
- Provide regular preventive maintenance.
- VOLATILE ORGANIC OR REACTIVE CHIICALS. If an organic or reactive chemical (e.g., formaldehyde) is believed to be the primary agent in an IAQ problem, potential controls to consider include additional dilution ventilation, removal or isolation of the offending material, and the transfer of sensitized employees.
- TOBACCO SMOKE IN AIR. OSHA has published a proposed rule for IAQ (including tobacco smoke in the workplace), and this rulemaking is likely to be completed in the near future. Smoking policies should include provisions for dedicated smoking areas. Dedicated smoking areas should be configured so that migration of smoke into nonsmoking areas will not occur. Such areas should:
- have floor-to-ceiling walls of tight construction;
- be under negative pressure relative to adjacent areas; AND
- be exhausted outside the building and not recirculated.
For more information on investigation of complaints, CSHO's should consult the NIOSH Guidance for Indoor Air Quality Investigation and the EPA guide Building Air Quality (1991).
American Conference of Governmental Industrial Hygienists (ACGIH). 1988. Industrial Ventilation, a Manual of Recommended Practice. 20th ed. Cincinnati, OH: American Conference of Governmental Industrial Hygienists.
Air Movement and Control Association (AMCA). 1988. AMCA Publication One. Arlington Heights, IL: Air Movement and Control Association.
American Society of Heating, Refrigerating, and Air-Conditioning Engineers (ASHRAE). Handbooks and Standards. Atlanta, GA: American Society of Heating, Refrigerating, and Air-Conditioning Engineers.
Sheet Metal and Air Conditioning Contractors National Association (SMACNA). SMACNA Publications. Arlington, VA: Sheet Metal and Air Conditioning Contractors National Association.
American National Standards Institute (ANSI) Standards:
Z9.1 - Open Surface Tanks Operation
Z9.2 - Fundamentals Covering the Design and Operation of Local Exhaust Systems
Z9.3 - Design, Construction, and Ventilation of Spray Finishing Operations
Z9.4 - Ventilation and Safe Practice of Abrasive Blasting Operations
Z9.5 - Laboratory Ventilation. Fairfax, VA: American Industrial Hygiene Association.
Burgess, W. A. et al. 1989. Ventilation and Control of the Work Environment. New York: Wiley Interscience.
Burton, D. J. 1989. Industrial Ventilation Workbook. Salt Lake City, UT: IVE, Inc.
Burton, D. J. 1990. Indoor Air Quality Workbook. Salt Lake City, UT: IVE, Inc.
Jorgensen, R. et al. 1983. Fan Engineering. 8th ed. Buffalo, NY: Buffalo Forge Co.
Homeon, W. C. L. 1963. Plant and Process Ventilation. New York: Industrial Press.
National Institute for Occupational Safety and Health (NIOSH). 1987. Guidance for Indoor Air Quality Investigations. Cincinnati: NIOSH.
OSHA Field Operations Manual. 1992. OSHA Instruction CPL 2.45B. Washington, D.C.: U.S. Government Printing Office.
U.S. Environmental Protection Agency (EPA). 1991. Building Air Quality.
SELECTION. Before an appropriate ventilation system can be selected, the employer should study emission sources, worker behavior, and air movement in the area. In some cases the employer may wish to seek the services of an experienced professional ventilation engineer to assist in the data gathering. Table III:3-5 shows factors to consider when selecting a ventilation system. Combinations of controls are often employed for HVAC purposes.
GENERAL EXHAUST (DILUTION) VENTILATION SYSTIS. General exhaust ventilation, also called dilution ventilation, is different from local exhaust ventilation because instead of capturing emissions at their source and removing them from the air, general exhaust ventilation allows the contaminant to be emitted into the workplace air and then dilutes the concentration of the contaminant to an acceptable level (e.g., to the PEL or below). Dilution systems are often used to control evaporated liquids.
To determine the correct volume flow rate for dilution (Qd), it is necessary to estimate the evaporation rate of the contaminant (qd) according to the following equation:
|where:||qd||=||evaporation rate in acfm|
|387||=||volume in cubic feet formed by the evaporation of one lb-mole of
a substance, e.g., a solvent
|MW||=||molecular weight of emitted material|
|lbs||=||lbs of material evaporated|
|min||=||time of evaporation|
|d||=||density correction factor|
The appropriate dilution volume flow rate for toxics is:
|where:||Qd||=||volume flow rate of air, in acfm|
|qd||=||evaporation rate, in acfm|
|Km||=||mixing factor to account for poor or random mixing
(Note: Km = 2 to 5; Km = 2 is optimum)
|Ca||=||acceptable airborne concentration of the material (typically half of the PEL).|
The number of air changes per hour is the number of times one volume of air is replaced in the space per hour. In practice, replacement depends on mixing efficiency. When using dilution ventilation:
- position exhausts as close to emission sources as possible;
- use auxiliary fans for mixing;
- make sure employees are upwind of the dilution zone; and
- add make-up air where it will be most effective.
LOCAL EXHAUST VENTILATION SYSTEMS. A typical local exhaust ventilation system is composed of five parts: fans, hoods, ducts, air cleaners, and stacks. Local exhaust ventilation is designed to capture an emitted contaminant at or near its source, before the contaminant has a chance to disperse into the workplace air.
FAN SELECTION. To choose the proper fan for a ventilation system, this information must be known:
- air volume to be moved;
- fan static pressure;
- type and concentration of contaminants in the air (because this affects the fan type and materials of construction); and
- the importance of noise as a limiting factor.
Once this information is available, the type of fan best suited for the system can be chosen. Many different fans are available, although they all fall into one of two classes: axial flow fans and centrifugal fans. For a detailed explanation of fans, see the ACGIH Industrial Ventilation Manual.
HOODS. The hood captures, contains, or receives contaminants generated at an emission source. The hood converts duct static pressure to velocity pressure and hood entry losses (e.g., slot and duct entry losses).
Hood entry loss (He) is calculated according to the following equation:
|VP||=||velocity pressure in duct|
||SPh|||=||absolute static pressure about 5 duct diameters down the duct from the hood.|
A hood's ability to convert static pressure to velocity pressure is given by the coefficient of entry (Ce), as follows:
To minimize air-flow requirements, the operation should be enclosed as much as possible, either with a ventilated enclosure, side baffles, or curtains. This helps both to contain the material and to minimize the effect of room air currents.
When using a capture or receiving hood, the hood should be located as close to the contaminant source as possible. Reducing the amount of contaminants generated or released from the process reduces ventilation requirements.
The hood should be designed to achieve good air distribution into the hood openings so that all the air drawn into the hood helps to control contaminants. Avoid designs that require that the velocities through some openings be very high in order to develop the minimum acceptable velocity through other openings or parts of the hood.
The purpose of most ventilation systems is to prevent worker inhalation of contaminants. For this reason, the hood should be located so that contaminants are not drawn through the worker's breathing zone. This is especially important where workers lean over an operation such as an open-surface tank or welding bench.
Hoods must meet the design criteria in the ACGIH Industrial Ventilation Manual or applicable OSHA standards. Most hood design recommendations account for cross-drafts that interfere with hood operation. Strong cross-drafts can easily reduce a hood's effectiveness by 75%. Standard hood designs may not be adequate to contain highly toxic materials.
The hood should be designed to cause minimum interference with the performance of work. Positioning access doors inside an enclosure that must be opened and closed often means that in practice the doors will be left open, and locating capture hoods too close to the process for the worker's convenience often means that the hood will be disassembled and removed. Hoods should never increase the likelihood of mechanical injury by interfering with a worker's freedom to move around machinery.
Two common misconceptions about hoods that are a part of local exhaust systems are:
- Hoods draw air from a significant distance away from the hood opening, and therefore they can control contaminants released some distance away. It is easy to confuse a fan's ability to blow a jet of air with its ability to draw air into a hood. Hoods must be close to the source of contamination to be effective.
- Heavier-than-air vapors tend to settle to the workroom floor and therefore can be collected by a hood located there. A small amount of contaminant in the air (1,000 ppm means 1,000 parts of contaminant plus 999,000 parts of air) has a resulting density close to that of air, and random air currents will disperse the material throughout the room.
Air flows turbulently through ducts at between 2,000-6,000 feet per minute (fpm). Ducts can be made of galvanized metal, fiberglass, plastic, and concrete. Friction losses vary according to ductwork type, length of duct, velocity of air, duct area, density of air, and duct diameter.
The design of the air cleaner depends on the degree of cleaning required. Regular maintenance of air cleaners increases their efficiency and minimizes worker exposure. Different types of air cleaners are made to remove particulates (e.g., precipitators, cyclones, etc.) and gases and vapors (e.g., scrubbers).
Stacks disperse exhaust air into the ambient environment. The amount of reentrainment depends on exhaust volume, wind speed and direction, temperature, location of intakes and exhausts, etc. When installing stacks:
- Provide ample stack height (a minimum of 10 ft above adjacent rooflines or air intakes);
- Place stack downwind of air intakes;
- Provide a stack velocity of a minimum of 1.4 times the wind velocity;
- Place the stack as far from the intake as possible (50 ft is recommended);
- Place the stack at least 10 ft high on most roofs to avoid recirculation; and
- Avoid rain caps if the air intake is within 50 ft of the stack.
MAKE-UP AIR SYSTIS. Exhaust ventilation systems require the replacement of exhausted air. Replacement air is often called make-up air. Replacement air can be supplied naturally by atmospheric pressure through open doors, windows, wall louvers, and adjacent spaces (acceptable), as well as through cracks in walls and windows, beneath doors, and through roof vents (unacceptable). Make-up air can also be provided through dedicated replacement air systems. Generally, exhaust systems are interlocked with a dedicated make-up air system.
Other reasons for designing and providing dedicated make-up air systems are that they:
- Avoid high-velocity drafts through cracks in walls, under doors, and through windows;
- Avoid differential pressures on doors, exits, and windows; and
- Provide an opportunity to temper the replacement air.
If make-up air is not provided, a slight negative pressure will be created in the room and air flow through the exhaust system will be reduced.
HVAC (heating, ventilating, and air-conditioning) is a common term that can also include cooling, humidifying or dehumidifying, or otherwise conditioning air for comfort and health. HVAC also is used for odor control and the maintenance of acceptable concentrations of carbon dioxide.
Air-conditioning has come to include any process that modifies the air for a work or living space: heating or cooling, humidity control, and air cleaning. Historically, air-conditioning has been used in industry to improve or protect machinery, products, and processes. The conditioning of air for humans has become normal and expected. Although the initial costs of air conditioning are high, annual costs may account only for about 1% to 5% of total annual operating expenses. Improved human productivity, lower absenteeism, better health, and reduced housekeeping and maintenance almost always make air-conditioning cost effective.
Mechanical air-handling systems can range from simple to complex. All distribute air in a manner designed to meet ventilation, temperature, humidity, and air-quality requirements established by the user. Individual units may be installed in the space they serve, or central units can serve multiple areas.
HVAC engineers refer to the areas served by an air handling system as zones. The smaller the zone, the greater the likelihood that good control will be achieved; however, equipment and maintenance costs are directly related to the number of zones. Some systems are designed to provide individual control of rooms in a multiple-zone system.
Both the provision and distribution of make-up air are important to the proper functioning of the system. The correct amount of air should be supplied to the space. Supply registers should be positioned to avoid disruption of emission and exposure controls and to aid dilution efforts.
Considerations in designing an air-handling system include volume flow rate, temperature, humidity, and air quality. Equipment selected must be properly sized and may include:
- outdoor air plenums or ducts
- supply fans and supply air systems
- heating and cooling coils
- humidity control equipment
- supply ducts
- distribution ducts, boxes, plenums, and registers
- return air plenums
- exhaust air provisions
- return fans
- controls and instrumentation
RECIRCULATION. Although not generally recommended, recirculation is an alternative to air exchanging. Where used, recirculation should incorporate air cleaners, a by-pass or auxiliary exhaust system, regular maintenance and inspection, and devices to monitor system performance. Key points to consider in the use of recirculation are shown in Table III:3-6.
acfm Actual cubic feet per minute of gas flowing at existing temperature and pressure. (See also scfm.)
ACH, AC/H (air changes per hour) The number of times air is replaced in an hour.
AIR DENSITY The weight of air in lbs per cubic foot. Dry standard air at T=68° F (20° C) and BP = 29.92 in Hg (760 mm Hg) has a density of 0.075 lb/cu ft.
ANIOMETER A device that measures the velocity of air. Common types include the swinging vane and the hot-wire anemometer.
AREA (A) The cross-sectional area through which air moves. Area may refer to the cross-sectional area of a duct, a window, a door, or any space through which air moves.
ATMOSPHERIC PRESSURE The pressure exerted in all directions by the atmosphere. At sea level, mean atmospheric pressure is 29.92 in Hg, 14.7 psi, 407 in w.g., or 760 mm Hg.
BRAKE HORSEPOWER (bhp) The actual horsepower required to move air through a ventilation system against a fixed total pressure plus the losses in the fan. bhp=ahp × 1/eff, where eff is fan mechanical efficiency.
CANOPY HOOD (Receiving Hood) A one- or two-sided overhead hood that receives rising hot air or gas.
CAPTURE VELOCITY The velocity of air induced by a hood to capture emitted contaminants external to the hood.
COEFFICIENT OF ENTRY (Ce) A measure of the efficiency of a hood's ability to convert static pressure to velocity pressure; the ratio of actual flow to ideal flow.
DENSITY CORRECTION FACTOR A factor applied to correct or convert dry air density of any temperature to velocity pressure; the ratio of actual flow to ideal flow.
DILUTION VENTILATION (General Exhaust Ventilation) A form of exposure control that involves providing enough air in the workplace to dilute the concentration of airborne contaminants to acceptable levels.
EVASE (pronounced eh-va-say) A cone-shaped exhaust stack that recaptures static pressure from velocity pressure.
FAN A mechanical device that moves air and creates static pressure.
FAN LAWS Relationships that describe theoretical, mutual performance changes in pressure, flow rate, rpm of the fan, horsepower, density of air, fan size, and sound power.
FAN CURVE A curve relating pressure and volume flow rate of a given fan at a fixed fan speed (rpm).
FRICTION LOSS The static pressure loss in a system caused by friction between moving air and the duct wall, expressed as in w.g./100 ft, or fractions of VP per 100 ft of duct (mm w.g./m; Kpa/m).
GAUGE PRESSURE The difference between two absolute pressures, one of which is usually atmospheric pressure.
GENERAL EXHAUST See Dilution Ventilation.
HEAD Pressure, e.g. "The head is 1 in w.g."
HOOD A device that encloses, captures, or receives emitted contaminants.
HOOD STATIC PRESSURE (SPh) The sum of the duct velocity pressure and the hood entry loss; hood static pressure is the static pressure required to accelerate air at rest outside the hood into the duct at velocity.
HVAC (HEATING, VENTILATION, AND AIR CONDITIONING) SYSTIS Ventilating systems designed primarily to control temperature, humidity, odors, and air quality.
INDOOR AIR QUALITY (IAQ), SICK-BUILDING SYNDROME, TIGHT-BUILDING SYNDROME The study, examination, and control of air quality related to temperature, humidity, and airborne contaminants.
in. w.g. (inches of water) A unit of pressure. One inch of water is equal to 0.0735 in. of mercury, or 0.036 psi. Atmospheric pressure at standard conditions is 407 in. w.g.
INDUSTRIAL VENTILATION (IV) The equipment or operation associated with the supply or exhaust of air by natural or mechanical means to control occupational hazards in the industrial setting.
LAMINAR FLOW (also Streamline Flow) Air flow in which air molecules travel parallel to all other molecules; laminar flow is characterized by the absence of turbulence.
LOCAL EXHAUST VENTILATION An industrial ventilation system that captures and removes emitted contaminants before dilution into the ambient air of the workplace.
LOSS Usually refers to the conversion of static pressure to heat in components of the ventilation system, e.g., "the hood entry loss."
MAKE-UP AIR See Replacement and Compensating Air.
MANOMETER A device that measures pressure difference; usually a U-shaped glass tube containing water or mercury.
OUTDOOR AIR (OA) Outdoor air is the "fresh" air mixed with return air (RA) to dilute contaminants in the supply air.
PITOT TUBE A device used to measure total and static pressures in an airstream.
PLENUM A low-velocity chamber used to distribute static pressure throughout its interior.
PRESSURE DROP The loss of static pressure across a point; for example, "the pressure drop across an orifice is 2.0 in. w.g."
REPLACEMENT AIR (also, Compensating Air, Make-Up Air) Air supplied to a space to replace exhausted air.
RETURN AIR Air that is returned from the primary space to the fan for recirculation.
scfm Standard cubic feet per minute. A measure of air flow at standard conditions, i.e., dry air at 29.92 in. Hg (760 mm Hg) (gauge), 68° F (20° C).
SLOT VELOCITY The average velocity of air through a slot. Slot velocity is calculated by dividing the total volume flow rate by the slot
area (usually, Vs = 2,000 fpm).
STACK A device on the end of a ventilation system that disperses exhaust contaminants for dilution by the atmosphere.
STANDARD AIR, STANDARD CONDITIONS Dry air at 68° F (20° C), 29.92 in Hg (760 mm Hg).
STATIC PRESSURE (SP) The pressure developed in a duct by a fan; the force in inches of water measured perpendicular to flow at the wall of the duct; the difference in pressure between atmospheric pressure and the absolute pressure inside a duct, cleaner, or other equipment; SP exerts influence in all directions.
SUCTION PRESSURE (See Static Pressure.) An archaic term that refers to static pressure on the upstream side of the fan.
TOTAL PRESSURE (TP) The pressure exerted in a duct, i.e., the sum of the static pressure and the velocity pressure; also called Impact Pressure, Dynamic Pressure.
TRANSPORT VELOCITY See Minimum Transport Velocity.
TURBULENT FLOW Air flow characterized by transverse velocity components as well as velocity in the primary direction of flow in a duct; mixing velocities.
VELOCITY (V) The time rate of movement of air; usually expressed as feet per minute.
VELOCITY PRESSURE (VP)
The pressure attributed to the velocity of air.
VOLUME FLOW RATE (Q) Quantity of air flow in cfm, scfm, or acfm.
- OSHA STANDARDS.
- HEALTH-RELATED VENTILATION STANDARDS. This list includes some, but not necessarily all, OSHA standards that address the control of employee exposure to recognized contaminants.)
|29 CFR 1910.94(a)||Abrasive blasting|
|29 CFR 1910.94(b)||Grinding, polishing and buffing operations|
|29 CFR 1910.94(d)||Open surface tanks|
|29 CFR 1910.252(f)(2)(i)(a)
|Ventilation for general welding and cutting--General|
|29 CFR 1910.252(f)(3)||Local exhaust hoods and booths|
|29 CFR 1910.252(f)(5)(ii)||Fluorine compounds--Maximum allowable concentration|
|29 CFR 1910.252(f)(12)||Cutting of stainless steels|
|29 CFR 1910.1003 to .1016||Carcinogens|
|29 CFR 1910.1025(e)(5)||Lead|
|29 CFR 1910.1027(f)(3)||Cadmium|
|29 CFR 1926.57(a)||Ventilation--General|
|29 CFR 1926.62(e)(3)||Lead|
|29 CFR 1926.63(f)(4)||Cadmium|
|29 CFR 1926.154(a)(1)||Temporary heating devices--Ventilation|
|29 CFR 1926.353(e)(1)||Ventilation and protection in welding, cutting and heating--General welding, cutting, and heating|
|29 CFR 1915.32(a)(2)||Toxic cleaning solvents|
|29 CFR 1915.51(f)(1)||Ventilation and protection in welding, cutting and heating--General welding, cutting, and heating|
|29 CFR 1918.93(a)(1)(iii)||Ventilation and atmospheric conditions|
- HEALTH-RELATED VENTILATION STANDARDS OTHER THAN AIRFLOW. This list includes some, but not necessarily all, OSHA standards that do not contain airflow requirements but are located in the health-related ventilation standards.
|29 CFR 1910.94(a)(3)(i)(d)||Abrasive blasting--Blasting cleaning|
|29 CFR 1910.94(a)(5)||Abrasive blasting--Personal protective equipment|
|29 CFR 1910.94(a)(6)||Abrasive blasting--Air supply and air compressors|
|29 CFR 1910.94(a)(7)||Abrasive blasting--Operational procedures and general safety|
|29 CFR 1910.94(d)(9)||Open surface tanks--Personal protection|
|29 CFR 1910.94(d)(10)||Open surface tanks--Special precautions for cyanide|
|29 CFR 1910.94(d)(11)||Open surface tanks--Inspection, installation and maintenance|
|29 CFR 1910.94(d)(12)||Open surface tanks--Vapor degreasing tanks|
- FIRE AND EXPLOSION-RELATED VENTILATION STANDARDS. This list includes some, but not necessarily all, OSHA standards that are intended to prevent fire and explosions.
|29 CFR 1910.94(c)||Ventilation--Spray finishing operations|
|29 CFR 1910.103(b)(3)(ii)(b)||Hydrogen--Gaseous hydrogen systems--Separate buildings|
|29 CFR 1910.103(b)(3)(iii)(b)||Hydrogen--Gaseous hydrogen systems--Special rooms|
|29 CFR 1910.103(c)(3)(ii)(b)||Hydrogen--Liquid hydrogen systems--Separate buildings|
|29 CFR 1910.103(c)(3)(iii)(b)||Hydrogen--Liquid hydrogen systems--Special rooms|
|29 CFR 1910.104(b)(3)(xii)||Oxygen--Bulk oxygen systems--Ventilation|
|29 CFR 1910.104(b)(8)(vii)||Oxygen--Bulk oxygen systems--Venting|
|29 CFR 1910.106(d)(4)(iv)||Flammable and combustible liquids--Container and portable tank storage--Design and construction of inside storage room--Ventilation|
|29 CFR 1910.106(e)(3)(v)||Flammable and combustible liquids--Industrial plants--Unit physical operations--Ventilation|
|29 CFR 1910.106(f)(2)(iii)(a)||Flammable and combustible liquids--Bulk plants--Building--Ventilation|
|29 CFR 1910.106(h)(3)(iii)||Flammable and combustible liquids--Processing plants--Processing building--Ventilation|
|29 CFR 1910.107(b)(5)(i)||Spray finishing using flammable and combustible materials--Spray booths--Dry type overspray collectors|
|29 CFR 1910.107(d)(1) and (2)||Spray finishing using flammable and combustible materials--Ventilation--Conformance--General|
|29 CFR 1910.107(i)(9)||Spray finishing using flammable and combustible materials--Electrostatic hand spraying equipment--Ventilation|
|29 CFR 1910.108(b)(1) and (2)||Dip tanks containing flammable combustible liquids--Ventilation--Ventilation combined with drying|
|29 CFR 1910.307||Hazardous (classified) locations|
- EXCEPTIONS TO 25% OF THE LEL FOR FIRE AND EXPLOSION-RELATED STANDARDS. This list includes but is not limited to OSHA standards that allow concentrations of flammable materials no greater than 10% of the LEL.
|29 CFR 1915.12(a)(2)||Precautions before entering--Flammable atmospheres and residues|
|29 CFR 1915.13(a)(2)||Cleaning and other cold work (flammable vapors)|
|29 CFR 1915.35(b)(1), (2), (3)||Painting--Paints and tanks coatings dissolved in highly volatile, toxic and/or flammable solvents|
|29 CFR 1915.36(a)(2)||Flammable liquids ventilation|
|29 CFR 1926.803(i)(2)||Compressed Air--Ventilation and air quality--(Tunnels)|
- SPECIAL CONDITIONS STANDARDS. This list includes some but not necessarily all OSHA standards that involve confined space operations and/or high-hazard contaminants specifically designated in the standard.
|29 CFR 1910.252(c)(2)(i)(c)||Welding, cutting and brazing--Health protection and ventilating--Ventilation for general welding and cutting--General|
|29 CFR 1910.252(c)(4)||Welding, cutting and brazing--Health protection and ventilating--Ventilation in confined spaces|
|29 CFR 1910.252(c)(5)(i)||Welding, cutting and brazing--Fluorine compounds|
|29 CFR 1910.252(c)(6)(i)||Welding, cutting and brazing--Zinc--Confined spaces|
|29 CFR 1910.252(c)(7)(i)||Welding, cutting and brazing--Lead--Confined spaces|
|29 CFR 1910.252(c)(8)||Welding, cutting and brazing--Beryllium|
|29 CFR 1910.252(c)(9)||Welding, cutting and brazing--Cadmium|
|29 CFR 1910.252(c)(10)||Welding, cutting and brazing--Mercury|
|29 CFR 1926.154(a)(2)||Temporary heating devices--Ventilation|
|29 CFR 1926.353(b)(1)||Ventilation and protection in welding, cutting and heating--Welding, cutting and heating in confined spaces|
|29 CFR 1926.353(c)(1) and (2)||Ventilation and protection in welding, cutting and heating--Welding, cutting or heating of metals of toxic significance|
|29 CFR 1926.800(k)||Tunnels and shafts--Air quality and ventilation|
|29 CFR 1915.12(b)(2)||Precautions before entering--Toxic atmospheres and residues|
|29 CFR 1915.12(c)(2)||Precautions before entering--Oxygen deficient atmospheres|
|29 CFR 1915.12(d)||Precautions before entering--Exceptions|
|29 CFR 1915.34(a)(4)||Mechanical paint removers--Power tools--(paint dust)|
|29 CFR 1915.51(c)(3)||Ventilation and protection in welding, cutting and heating--Welding, cutting and heating confined spaces|
|29 CFR 1915.51(d)(1) and (2)||Ventilation and protection in welding, cutting and heating--cutting or heating of metals of toxic significance.|
- CONSENSUS STANDARDS.
|ASHRAE 52-76||ASHRAE||Methods of Testing Air-Cleaning Devices Used in General Ventilation for Removing Particulate Matter|
|NFPA||Installation of Blower and Exhaust Systems for Dust, Stock, Vapor Removal or Conveying (1983)|
|ANSI Z9.2-1979||AIHA||Fundamentals Governing the Design and Operation of Local Exhaust Systems|
|Practices for Ventilation and Operation of Open-Surface Tanks|
|ANSI Z9.3-1964||ANSI||Safety Code for Design, Construction, and Ventilation of Spray Finishing Operations (reaffirmed 1971)|
|ANSI||Ventilation and Safe Practices of Abrasives Blasting Operations|
|ANSI Z9.5-1992||AIHA||Laboratory Ventilation|
|Standards Handbook Electric Fans (1977)|
|ASHRAE||Laboratory Methods of Testing Fans for Rating|
|ASHRAE||Methods of Testing Dynamic Characteristics of Propeller Fans--Aerodynamically Excited Fan Vibrations and Critical Speeds|
|AMCA 210-74||AMCA||Laboratory Methods of Testing Fans for Rating Purposes|
|AMCA 99-2404-78||AMCA||Drive Arrangement for Centrifugal Fans|
|AMCA 99-2406-83||AMCA||Designation for Rotation and Discharge of Centrifugal Fans|
|AMCA 99-2407-66||AMCA||Motor Positions for Belt or Chain Drive Centrifugal Fans|
|AMCA 99-2410-82||AMCA||Drive Arrangement for Tubular Centrifugal Fans|
|SMACNA||SMACNA||Round Industrial Duct Construction|
|SMACNA||SMACNA||Rectangular Industrial Duct Construction|
|NFPA 68||NFPA||Guide for Explosion Venting|
|NFPA 204M||NFPA||Guide for Smoke and Heat Venting|
|SMACNA||SMACNA||Guide for Steel Stack Design and Construction (1983)|
|NFPA 96||NFPA||Vapor Removal from Cooking Equipment (1984)|
|NFPA-88A, 88B||NFPA||Parking Structures (1979); Repair Garages (1979)|
|ASHRAE 62-1989||ASHARAE||Ventilation for Acceptable Indoor Air Quality|
- SOURCES OF CONSENSUS STANDARDS.
Copies of the consensus standards are published and available directly from the organization issuing the standard. A minimal fee is often required.
|ACGIH||American Conference of Governmental Industrial Hygienists
6500 Glenway Ave., Bldg. D-5
Cincinnati, OH 45211
|AIHA||American Industrial Hygiene Association
2700 Prosperity Ave., Suite 250
Fairfax, VA 22031-4319
|AMCA||Air Movement and Control Association
30 W. University Dr.
Arlington Heights, IL 60004
|ANSI||American National Standards Institute
New York, NY 10018
|ASHRAE||American Society of Heating, Refrigeration and Air-Conditioning Engineers, Inc.
1791 Tullie Circle, N.E.,
Atlanta, GA 30329
|NFPA||National Fire Protection Association
Quincy, MA 02269
|SMACNA||Sheet Metal and Air Conditioning Contractors' National Association
8224 Old Courthouse Rd.
Vienna, VA 22180
|UL||Underwriters Laboratories Inc.
333 Pfingsten Rd.
Northbrook, IL 60062
Most of the following checks can be made by visual observation and do not require extensive measurements.
If air flow is low in hoods, check:
- Fan rotation (reversed polarity will cause fan to run backwards; a backward-running centrifugal fan delivers only 30-50% of rated flow);
- Fan RPM;
- Slipping belt;
- Clogged or corroded fan wheel and casing;
- Clogged ductwork (high hood static pressure and low air flow may indicate restricted ducts; open clean-out doors and inspect inside ducts);
- Closed dampers in ductwork;
- Clogged collector or air cleaning devices;
- Weather cap too close to discharge stack (a 3/4 duct- diameter gap should exist between cap and stack; weather caps are not recommended);
- Poorly designed ductwork (short radius elbows); (branch entries enter main duct at sharp angles); (duckwork diameter too small for the air-flow needed; and
- Lack of make-up air (high negative pressures affect propeller fan system output; lack of supplied make-up air causes high airflow velocities at doors and windows).
If air flow is satisfactory in a hood but contaminant control is poor, check:
- Crossdrafts (from process air movements); (worker-cooling fans and air-supply systems); (open doors and windows);
- Capture velocity (work operation too far from hood opening);
- Hood enclosure: (door, baffles, or sides may be open or removed); and
- Hood type: (canopy hoods are inappropriate for toxic materials